---
id: 2025-11-04T14:52:05-0500
title: 2025-11-04 14:52:05
tags:
  - occupational/closeout
  - occupational/takeoff
  - status/complete
  - type/minutes
daily: "[[2025-11-04]]"
---
# 2025-11-04 14:52:05

### Belle Meade Director Review

[[estimating-director-review]] for [[belle-meade-plaza]]
lead by [[corwin-fluit]],
attended by [[joel-jansen]] and myself.

#### Takeoff Review

Reviewed takeoff by system.

##### Retail Village Temporary Power

Joel changed square foot budgets to temporary pole budgets only
due to minimal scope (warm shell).

##### Generator Scope

Confirmed generator quotes include furnishing docking station.

##### Feeder Lengths

Confirmed validity of longer feeder lengths:
Generator to Tower B

##### Grounding

Takeoff appears to be missing some or all grounding.
To be added if necessary.

##### Subfeed Sizing

Based on ampacity, subfeeds are oversized.
Sizing was per feeder schedule.
Takeoff approved unchanged.

##### Undercabinet Wiremold

Multi-outlet assemblies above unit kitchen countertops were not taken off,
nor was branch wiring for the same.
Joel to confirm takeoff requirement with bid.

##### Amenity Homeruns

No homeruns for amenity lighting or electrical were taken off.
Joel to add these.

> [!info] Circuits per Raceway
> Corwin stated that---assuming no overriding specification---
> up to 6 circuits per raceway are permissible.

##### Lighting Control

Lighting control takeoff was reviewed,
no changes were recommended.

> [!info] Lighting Control Pre-Work
> Corwin stated that with the imminent changes to lighting control takeoff,
> it will be necessary for estimators to more intently consider the design:
> noting quantities of lighting zones and controllers,
> even where not explicitly shown.

##### Telecom

Confirmed unit telecom requirements.

Backbone was mistakenly taken off in Telecom.

##### Retail Fire Alarm

Retail village fire alarm devices were taken off free-air,
Joel to substitute for EMT.

#### Extension Review

Reviewed extension quantities and costs.
Of particular note were:

* conduit
* wire
* cable
* wiring devices

#### Labor Plan Review

Hours per square foot was lower than expected,
this was rationalized as being due
to the relatively high portion of garage and shell retail space.

%%
"Openings per unit" was another metric considered---
higher than expected in this case---
however I didn't catch the significance of this.
%%
