---
id: 2026-02-11T12:12:16-0500
title: 2026-02-11 12:12:16
tags:
  - occupational
  - status/draft
daily: "[[2026-02-11]]"
up: "[[conest-pre-takeoff-email-template]]"
---
# 2026-02-11 12:12:16

%%
Implementation of [[conest-pre-takeoff-email-template]]
for [[1990-k-street]]
%%

Hello Team,

Below is a comprehensive list of means & methods for **1990 K Street**.
Please confirm you have received this email
and respond with any questions or comments.

* **Takeoff Request Stage:** Full Takeoff
    %% Stage 1, Stage 1 + Units, Full takeoff %%
* **Delivery Method:** Plans & Specs
    %% Plans & Specs, Design Build, Design Assist, P&S with Approved VE %%
* **Document Stage:** Permit
    %% DD, CD, Permit, GMP, Bid, Awarded %%
* **Drawings Date:** 2025-12-05
* **Project Manual Date:** 2025-12-05
* **Proposal Date:** 2026-01-22

### Project Specification Callouts

%% Put page of Drawing or PM after answer %%

* **Conduit:**
    * EMT Fittings: Set-screw _---Spec 260533.13 (p. 1423)_
    %% GRC, coupling specs, etc. %%

* **Wire:**
    * Material: Aluminum 100A and larger _---E021 "ALUMINUM FEEDER SCHEDULE" Note 1(b)_
    * Acceptable Manufacturers: _---Spec 260519 (p. 1384)_
        * Alpha Wire; Brand of Belden, Inc.
        * Belden Inc.
        * Cerro Wire LLC
        * Encore Wire Corporation
        * General Cable; Prysmian Group North America
        * Okonite Company
        * Service Wire Co.
        * Southwire Company, LLC
        * WESCO

* **MC Cable:**
    * Application: Concealed feeders and branch circuits _---Spec 260519 (p. 1389)_
        %% Branch homeruns only; Not permitted %%
    * Acceptable Manufacturers: _---Spec 260519 (p. 1385-1386)_
        * AFC Cable Systems; Atkore International
        * Alpha Wire; Brand of Belden, Inc.
        * Belden Inc.
        * Cerro Wire LLC
        * Encore Wire Corporation
        * General Cable; Prysmian Group North America
        * Okonite Company
        * Southwire Company, LLC
        * WESCO
    * ==Conductors: Copper _---Spec 260519 (p. 1386)_==
    * ==Armor: Steel _---Spec 260519 (p. 1386)_==
    * ==Jacket: PVC _---Spec 260519 (p. 1386)_==

* **Steel Box Depth:**
    * Telecom: 2-1/8" _---Spec 270500 (p. 1673)_
    * Security: 2-1/8" _---Spec 280500 (p. 1753)_
    * Other Applications: Not specified
    %% 1-1/2", 2-1/8" %%

* **Floor Boxes:** Sheet metal with brass or aluminum covers _---Spec 262719 (p. 1541)_

* **Wiring Devices:**
    * Units:
        * Current rating: Unspecified. Assuming 15A for takeoff.
        * Standard/Decora: Unspecified. Assuming Toggle/Duplex for takeoff.
        %% 15A Decora %%
    * BOH/Common Areas:
        * Current rating: Unspecified. Assuming 20A for takeoff.
        * Standard/Decora: Unspecified. Assuming Toggle/Duplex for takeoff.
      %% 20A Toggle/Duplex %%

* **Switchboards:**
    * Acceptable Manufacturers: _---Spec 262413 (p. 1502)_
        * ABB, Electrification Business
        * Eaton
        * Siemens Industry, Inc., Energy Management Division
        * Square D; Schneider Electric USA
        * General Electric
    * Bus Material: Aluminum _---Spec 262413 (p. 1503)_
    * Interrupting Current Rating: Not specified.

* **Distribution Panelboards:**
    * Acceptable Manufacturers: _---Spec 262413 (p. 1514-1515)_
        * Eaton
    * Bus Material: Aluminum _---Spec 262413 (p. 1513)_
    * Breaker Types: Bolt-on _---Spec 262413 (p. 1515)_
        %% Snap-on, bolt on %%
    * Interrupting Current Rating: Not specified.

* **Load Centers:**
    * Acceptable Manufacturers: _---Spec 262413 (p. 1514-1515)_
        * ABB, Electrification Business
        * Eaton
        * Siemens Industry, Inc., Energy Management Division
        * Square D; Schneider Electric USA
    * Bus Material: Aluminum _---Spec 262413 (p. 1513)_
    * Breaker Types: Plug-in _---Spec 262413 (p. 1515)_
        %% Snap-on, bolt on %%
    * Interrupting Current Rating: Not specified.
    * ==Covers shall be factory-applied white paint.== _---Dwg. E401-E405 "ELECTRICAL DRAWING NOTES" (P)_

* **Transformers:**
    * Winding Material: Aluminum _---Spec 262213 (p. 1495)_
    * K-Rating: Not specified.
    %% Windings AL or CU, K-rating %%

* **Generator:** (1) 600kW Diesel
    * Enclosure Specs: Level 2 Sound Attenuating Weatherproof Enclosure _---Dwg. E014_
    * Remote Tank: None shown or specified.
    * Tank Size: 24hrs at 100% load _---Spec 263213.13 (p. 1604)_
    * Load Banks: Internal, 50% load _---Dwg. E014, Spec 263213.13 (p. 1608)_
    * Acceptable Manufacturers: _---Spec 263213.13 (p. 1600)_
        * Caterpillar, Inc.; Electric Power Division
        * Cummins Power Generation
        * Generac
        * Hipower Systems
        * Kohler Power Systems
        * Rolls-Royce Solutions America Inc

### Project Drawing/Detail Callouts

Dwg. IDS-01A "OUTLET SPECIFICATIONS": Screwless Cover

Dwg. IDS-01A "SWITCHING SPECIFICATIONS": Legrand Tru-Universal Rocker/Dimmers
(Is this for Amenity/Common Areas?)

<!--
* **Describe conflicts between drawings / proposal**
    %% Plans show CU feeders, proposal calls for aluminum; Specification grade devices, etc. %%

* **Cost drivers in details not shown elsewhere on plans**
    %% Assuming this refers to lighting control %%
-->

### PDI System Execution Plan

* **Primaries:** Conduit and wiring excluded. _---Proposal 2026-01-22, Ex. B, Exclusions, Line 27_
    %% Installation only, (9) 6" PVC %%

* **Secondaries:**
    * Schedule 40 PVC UG; _---Proposal 2026-01-22, Ex. B, Inclusions Line 54-55_
    * wiring excluded. _---Proposal 2026-01-22, Ex. B, Exclusions, Line 28_
    %% PVC UG, GRC Stub-ups, AL %%

* **Feeders:** PVC UG, EMT OH; AL 100A and larger; 2% voltage drop.
    %% PVC UG, EMT OH, AL over 100A, 2% VD %%
    %% Emergency Feeds MI Cable %%

* **Unit Subfeeds:** MC OH; size per E025-E028 meter bank schedules; 3% voltage drop.
    %% MC OH AL, VD per Chart on E5.01 %%

* **Units:**
    * DW/Disposal - Separate Circuit
    * Range - \#6/3
    * Kitchen Backsplash - Decora (Non-Combo Small Appliance Breakers)
    * 120V Smokes
    * EWH - \#8/2
    * VRF HVAC
    * 20A Toggle Switches
    * 15A Duplex Receptacles
    %% 15A Decora, Disposals, T-stat, Floor Boxes, Shade Control, Doorbells, Dimmer Switches, etc. %%

* **Telecom:**
    * 30" MSDE; _---T0.32/1 Note 3: "PRIMEX SOHOPRO P3000ND"_
    * (1) 1" innerduct to IDF. _---Proposal 2026-01-22, Ex. B, General Requirements, Line 114_
    %% 42" MSDE, No Cable Homeruns, (1) 1" Back to IDF, CAT6 with Stub-ups %%

* **EV Chargers:** (2) dual circuit chargers with conduit, wire, data rough-in, and equipment.
    %% (42) Conduit only, (56) Conduit & Wire, (20) Conduit, Wire & Equipment %%

* **Fire Alarm:** Devices PVC in-slab, Risers EMT.
    %% Free-air where allowed by code. EMT Risers. %%

* **DAS:** System per PDI DAS Design.
    %% Conduit only, Per PDI DAS Design %%

* **Low Voltage:** Free-air where allowed by code.
    %% Free-air where allowed by code. Stub-ups to accessible ceilings. %%

### Lighting Control

* **Basis of Takeoff:** Design per Plans and Specs _---Christian Pereiro 2026-02-11_
    %% Code Minimum per Energy Code Assigned, P&S, PDI Design %%

* **Area:** _---Dwg. E021 "AUTOMATED LIGHTING CONTROL - SEQUENCES OF OPERATIONS"_
    * BOH: Line Voltage Control, no dimming
    * Corridor: Digital Standalone Control, 0-10V dimming
    * Amenity: Digital Standalone Control, 0-10V dimming
    * Offices: Digital Standalone Control, 0-10V dimming, controlled receptacles as shown
    * Site/Landscape: Line Voltage Control, no dimming
    * Garage: Digital Standalone Control, 0-10V dimming
    %% Assign Method to Areas: Line Voltage, Low-Voltage Stand Alone or Centralized System %%

Takeoff will utilize assemblies including
conduit rough-in, Cat5e cable, and device labor.

### Tasks/Quotes Needed for WBS

%% Delete any completed %%

%% * Electrical Constructability Review %%
%% * Electrical VDC %%
* Coordination Study
%% * DAS Public Safety Raceway Design %%

<!--
DAS Public Safety Raceway Design is necessary
if we own DAS pathways but not the system,
since if we own the system,
the raceway design will be included in the Systems quote.
-->

Thank you,
