---
id: 2026-05-28T09:17:29-0400
title: 2026-05-28 09:17:29
tags: []
daily: "[[2026-05-28]]"
---
# 2026-05-28 09:17:29

## Mariposa Spa Electrical

[[303-mariposa-residence]]

~~E2.01 we have 10 pump connections~~
~~roughly near where the spa drawings put the pool equipment room~~
~~not shown on mech, plumbing, otherwise~~
~~despite Keynote 4 "SEE MECHANICAL WATER PIPING DIAGRAM FOR EXACT LOCATIONS OF PUMPS."~~
~~We could assume that these are intended for the pool equipment~~
~~and delete the takeoff.~~[^1]

[^1]: M3.00, being a diagram, does not show exact locations,
    _but does show the pumps being used for domestic water._
    (Also the diagram suggests
    that the pumps may be spread much far than implied by Electrical,
    that our takeoff may be missing a large amount of cable.)
    (Also four water heaters are shown
    which were not shown on electrical.)

 SP400 shows an electrical panel Keynote 16

> [!quote] SP400 Keynote 16
> NOT SHOWN ON PLANS.
> PROVIDE DISCONNECTS IF PANEL IS NOT IN EQUIPMENT ROOM.
> IF ELECTRICAL PANEL IS LOCATED IN EQUIPMENT ROOM,
> THEN THE PANEL MUST BE NEMA-4X RATED...

No panel schedule is provided.

SP400 Pool Equipment Room is not shown
on the Arch, Elec, Mech, or Plumbing sets.
It is not shown enclosed, even on the Spa set.
It seems like the Spa set was done last
with no coordination with other disciplines.

> With no other information
> I'd assume PVC, LFMC, and NEMA 4X disconnects
> to all equipment shown on SP400
> from the Garage panels.

Water Feature plans are a similar case.

> [!quote] [[joshua-komis]] 2026-05-28 around 10:30 (pp.)
> Assume a single-point connection
> to a pool equipment panel.
> 100A for the spa.
> Scope for equipment downstream of the panel
> should be excluded.

Neither [[jared-defanti]] nor I am satisfied with this answer.
This would mean excluding a significant number of connections.

Around 13:10 we spoke to [[joel-jansen]] about the issues.
He tended to agree with us
that the drawings suggested the EC would be responsible for more,
but said he would confirm with [[christian-pereiro]].

Christian directed us to respect Komis's direction.
