---
id:
aliases: []
tags:
  - authorship/original
  - destiny/permanent
  - occupational/takeoff/units
  - status/draft
  - type/guide
title: Unit Takeoff
---
# Unit Takeoff

> [!important]
> Complete [[pre-takeoff-research]],
> including [[wiring-method-selection]] and [[wiring-device-research]],
> before beginning takeoff.

> [!info]
> See [[multi-family-dwellings]].

## Takeoff

> [!tip] Preparing for Unit Takeoff
> Units generally have very little variation.
> It is usually best to copy-paste takeoffs
> rather than re-build them for each unit.

1. Kitchen and Bath
2. General assemblies
3. Low Voltage
4. Lighting Fixtures
5. Lighting Control

> [!tip]
> It may be more efficient and neat to not copy switches,
> instead keeping the switch assembly list open
> and creating them new for each unit,
> since the types required can vary greatly between units.

### Load Centers

| Rating  | Assembly                                                                           |
| ------- | ---------------------------------------------------------------------------------- |
| <= 100A | `DIST PANELS & UNIT LOAD CENTERS`/`UNIT LOAD CENTERS - ...`/`... UNIT LOAD CENTER` |
|  > 100A | `DIST PANELS & UNIT LOAD CENTERS`/`UNIT LOAD CENTERS - ...`/`... BREAKER PNL`      |

Include terminations per [[switchgear]].

### Shade Control

### VTAC Units

Used in lieu of individual split systems.

### Dedicated Circuit Receptacles

For N5-15R/N5-20R receptacles serving fixed equipment such as:

* refrigerators
* gas ranges
* microwaves
* clothes washers
* hood fans

use single receptacle assemblies, even where shown as duplex.

`COMMON ASSEMBLIES`/`UNITS - MC CABLE ASSEMBLIES`/`KITCHEN & BATH  ASSEMBLIES - METAL STUD`/`SGL REC ...`

### Air Sealing

* LEED Silver
* Mid-Atlantic jobs
* "Draft Proof Box"

`ITEM DATABASE`/`BOXES & CABINETS`/`BOXES - VAPOR`/`...`

`COMMON ASSEMBLIES`/`UNITS - MC CABLE ASSEMBLIES`/`GENERAL  ASSEMBLIES - METAL STUD`/`UNIT MISC ITEMS - MC - ADJUST ACCORDINGLY`

### Islands

Use 1 "SLAB / DECK" receptacle for every 2 circuits in the island.

`COMMON ASSEMBLIES`/`UNITS - MC CABLE ASSEMBLIES`/`... RECEPTACLE TAMPER RESISTANT ...`/`... (METAL STUD) - 20' 3/4" PVC, ENT, 3#12 THHN`

Use standard MC assemblies for remaining devices.

### Bidet Toilets, Whirlpool Baths, etc.

`COMMON ASSEMBLIES`/`MECHANICAL CONNECTIONS (UP TO 100A)`/`PVC - LT NM FLEX (CARFLEX)`/`20A 1PH MECH CONN (100') 3/4" PVC 3#12 - CARFLEX`

### "High-Lows"

`COMMON ASSEMBLIES`/`TELECOM SYSTEMS`/`UNIT DATA  - TELECOM`/`HIGH-LOW - TV SCOOP 1 1/2" ENT - NO CABLE`

Eaton 35M2W

### Telecom Homeruns

Included in MSDE.

### Fire Alarm Devices

#### Residential

##### Smoke Detectors & CO Detectors

For smoke detectors and CO detectors where 120V (most common):

`COMMON ASSEMBLIES`/`UNITS - MC CABLE ASSEMBLIES`/`GENERAL  ASSEMBLIES - METAL STUD`/`UNIT SMOKE DETECTOR W/ CO DETECTOR ...`

For ADA units:

`COMMON ASSEMBLIES`/`UNITS - MC CABLE ASSEMBLIES`/`GENERAL  ASSEMBLIES - METAL STUD`/`UNIT SMOKE DETECTOR / VISUAL SIGNAL ...`

##### Additional Signaling Devices

==use free air devices==
